Centex Mechanical Air & Heat is a family-owned and operated HVAC company serving the residents of Bastrop, TX. We’ve lived here and worked here since 1984.
Our business philosophy is “neighbors serving neighbors.” We treat you how we want to be treated. Read reviews from your neighbors in Bastrop, TX to see how we live that philosophy every day.
for Bastrop, TX
Our Reviews by City
Fred - Bastrop, TX
Kim - Bastrop, TX
Everyone on the team was so great. I would highly recommend them to anyone. Excellent customer service, price and very timely manner.
Ray - Bastrop, TX
Very professional. Cleaned up totally before leaving.
Response from Centex Mechanical Air and Heat:
Thank you, Mr. Boyd. We appreciate the opportunity to serve you. We're very happy to hear you're as happy with Iban and the guys as we are.
The Thrift Stop - Bastrop, TX
Outstanding workmanship and AC product provided by this team from Centex! We were amazed at how quick and professional everything was to install the AC unit! We'll definitely be recommending them to other customers as well. Thanks again from The Thrift Stop!
Joy - Bastrop, TX
HVAC contractors Bastrop. Outdoor fan motor extremely hot and over amping. Replace the outdoor exhaust removal system, blade, voltage enhancement system, and voltage distribution. System is cooling.
Commercial HVAC service. System is running but the blade and after market exhaust removal system is causing the head pressure to go very high. Replace the exhaust removal system and blade, clean both heat transfer coils, and replace both voltage enhancement system. System is operating properly at this time.
Commercial AC service Bastrop. Bugs got into the voltage distribution system and the voltage enhancement system is low. Replace the voltage enhancement, voltage distribution, and add a pound of r410a to get the charge to the manufacturer's specifications. System is working properly.
Commercial AC service Bastrop. System is running but the blade and after market exhaust removal system is causing the head pressure to go very high. Replace the exhaust removal system and blade, clean both heat transfer coils, replace both voltage enhancement system. System is working properly.
Clogged drain on a Trane heat pump system.