Centex Mechanical Air & Heat has served our neighbors in Cedar Creek, TX and the surrounding areas since 1984. Our goal is to always provide competitve prices and expert service.
Read our reviews and find out why your neighbors have considered us to be their nearby air conditioning and heating company in Cedar Creek, TX for over 30 years.
for Cedar Creek, TX
Our Reviews by City
John - Cedar Creek, TX
Centex Heat Pump Install
Mike - Cedar Creek, TX
Centex showed up on time, employees were very courteous, they were all well groomed and looked professional, time was taken to explain the system/parts, work areas were clean when they left, and one employee even took the time and initiative to fix the chain on my daughters bike before he left! Very happy with the system they installed so far. Head and shoulders better than the old system I had, which Centex installed in 2001. That system lasted 16 years, so hoping this one gives the same service life or better.
Tim - Cedar Creek, TX
High quality all the way around - people, product, installation. I needed a quick replacement of the HVAC unit in a rental house. Centex Mechanical came out to inspect the existing unit (10 year old unit which was nothing but trouble from the day it was installed by another vendor). The technician explained the issues and suggested replacement options. Centex provided a great set of bids and I scheduled the install. Iban, Terrick and Julian showed up at 8:00am as scheduled and went right to work removing the old unit, pulling new control wiring and installing the new equipment. Everything was up and running by 2:00 in the afternoon.
Stephen - Cedar Creek, TX
Hvac one time system inspection on a Goodman heat pump system.
Hvac repair on a Goodman gas pack system.
Replacement of the outdoor contactor and capacitor on a Goodman heat pump system.
Drain cleared on a carrier performance series heat pump system.
Replacement of the drain line on a Bryant heat pump system.
Hvac cleaning on a carrier green speed heat pump system
Hvac repair on a carrier heat pump system. Capacitor was bad on the outdoor system
Coil replaced on two carrier heat pump systems.
Replacement of the low voltage fuse on a Rheem heat pump system.