Centex Mechanical Air & Heat is a local, family-owned HVAC business that has been serving the Central Texas area for 36 years. When you’re looking for the best heating and air conditioning services in Paige, TX, look for us!
We have a tradition of neighbors helping neighbors through excellent service and excellent pricing. Read our reviews and find out why your neighbors consider us to be the best local heating and air company in Paige, TX!
for Paige, TX
Our Reviews by City
Canell - Paige, TX
Levitre - Paige, TX
Connie - Paige, TX
So far all my experiences with the Centex team (Gene, Darryl, Iban,Julian, Terrick, Dillion, Celeana) have been great. The install team today were very professional and did a great job installing my new Carrier! Highly recommend Centex Mechanical!
Extender - Paige, TX
I found that the air conditioning system was frozen solid. I defrosted the AC system and checked the charge which I found was ok but the suction was off because the coil was extremely dirty and causing low airflow. I spoke with the client about her different options and she chose the hk6c. We need to call and schedule a day to come out and clean this will take 1 person about 3 hours we will pull and clean the coil.
Upon arrival found the voltage enhancement system was bad talked to client and pick HN4A at this time
Installed new communicating air handler with infinity thermostat, we rebuilt the stand, installed a NIM, cut in a new return air grill and replaced the other, added a filter base, installed surge protection on the downstairs and upstairs, after the HVAC system was up and running I tested the charge and found it was at manufactures specifications. I spoke with the client about indoor air quality and maintenance. Client has signed up for maintenance and is looking into the Reme halo. Asked for a quote.
Reflare all Connections on Master AC system after the reflareing we pressure tested and found a major leak on the indoor 18000btu ducted unit. We also sealed the ducted unit in the bedroom. I have a phone call into Insco to check on the warranty and availability of this coil. I will get back with the client when we get all the info. We replaced the 18000 btu ducted coil , pressurized the system and pulled a vacuum down to 500 microns. I then refilled the HVAC system with 19 pounds of r410a and made sure the air conditioning system was cooling properly.
Performed cooling maintenance evaluation. The air conditioning system is operating at manufacture specifications at this time. .
I found that the upstairs system was extremely dirty, extremely low on charge and an older system. I recommend due to the age and condition of the system that the client replaced the whole system. Client would like a consultation on a new system. The reasoning I didnâ€™t give pricing for a new system is because itâ€™s in a limited space and the client also like the thought of mini splits. Please set up a time for gene to come out and give a quote.
Performed the HL1A on system and AC is operating at manufacture specifications at this time.
Kim.firstname.lastname@example.org I found that the indoor hvac system had a bad air circulation system. I spoke to the client about his different options and he chose the Hc6a, surge protection and comf1 service plan. I replaced the motor and added surge protection on the indoor system. After the repair I checked the split and found it was 18 degrees. System is now operating properly.
I found that the air conditioning system had a clogged drain line and the indoor coil was extremely dirty. I recommend clearing the drain line and cleaning the coil. Client only wanted to clear the drain line at this time. I cleared the drain line and ran water/vinegar mix after clearing to make sure it was flowing properly.
Installed start assist kit in the system. OFFICE NOTE: We have installed the wrong start assist kit. Need to make a return visit to install the correct one.
Hvac repair on a Rheem heat pump system.
Cleaning of an evaporator coil on a carrier heat pump system.
Carrier air conditioner maintenance
Cleaning of the indoor air circulation system on a Mitsubishi mini split system.